So the electrical inspector came today and went over all the things on his list. Actually, he hadn’t written everything down and appreciated me calling the out those items. After he was done, he wrote out a yellow ticket and stuck it to one of the main panels and congratulated me. Niiiice to get a second final taken care of! I set the line from the main level condensate pump this morning and called for a final plumbing inspection. Hopefully that’ll be in the next day or two aso I can then call for the temp CO.
Finished assembling the barn door I’ve been making for our master bath, fasten the last hand rail, and cut blocks for the the beams to be fastened to. Trying to lay out just where to set the beams on the ceiling. Thought I had it and then realized that there was a return air vent in the way. So I’ll look at it with a fresh mind in the morning.
Login to Reply